U.S. Code of Federal Regulations
Regulations most recently checked for updates: May 20, 2019
Each weld that is unacceptable under § 192.241(c) must be repaired as follows:
(a) If it is feasible to take the segment of transmission line out of service, the weld must be repaired in accordance with the applicable requirements of § 192.245.
(b) A weld may be repaired in accordance with § 192.245 while the segment of transmission line is in service if:
(1) The weld is not leaking;
(2) The pressure in the segment is reduced so that it does not produce a stress that is more than 20 percent of the SMYS of the pipe; and
(3) Grinding of the defective area can be limited so that at least
(c) A defective weld which cannot be repaired in accordance with paragraph (a) or (b) of this section must be repaired by installing a full encirclement welded split sleeve of appropriate design.