U.S. Code of Federal Regulations
Regulations most recently checked for updates: May 20, 2019
(a) Except for rupture discs, each pressure relieving device in a compressor station must be inspected and tested in accordance with §§ 192.739 and 192.743, and must be operated periodically to determine that it opens at the correct set pressure.
(b) Any defective or inadequate equipment found must be promptly repaired or replaced.
(c) Each remote control shutdown device must be inspected and tested at intervals not exceeding 15 months, but at least once each calendar year, to determine that it functions properly.