U.S. Code of Federal Regulations
Regulations most recently checked for updates: Mar 19, 2019
(a) Each cast iron caulked bell and spigot joint that is subject to pressures of more than 25 psi (172kPa) gage must be sealed with:
(1) A mechanical leak clamp; or
(2) A material or device which:
(i) Does not reduce the flexibility of the joint;
(ii) Permanently bonds, either chemically or mechanically, or both, with the bell and spigot metal surfaces or adjacent pipe metal surfaces; and
(b) Each cast iron caulked bell and spigot joint that is subject to pressures of 25 psi (172kPa) gage or less and is exposed for any reason must be sealed by a means other than caulking.