U.S. Code of Federal Regulations
Regulations most recently checked for updates: Oct 26, 2020
(a) For the purpose of this subpart, an industrial system is a system that -
(1) Is not a ship's service load, as defined in § 111.10-1;
(2) Is used only for the industrial function of the vessel;
(3) Is not connected to the emergency power source; and
(4) Does not have specific requirements addressed elsewhere in this subchapter.
(b) An industrial system that meets the applicable requirements of NFPA NEC 2002 (incorporated by reference, see 46 CFR 110.10-1) must meet only the following:
(1) The switchgear standards in part 110, subpart 110.10, of this chapter.
(2) Part 110, subpart 110.25, of this chapter - Plan Submittal.
(3) Subpart 111.01 of this part - General.
(4) Subpart 111.05 of this part - Equipment Ground, Ground Detection, and Grounded Systems.
(5) Sections 111.12-1(b) and 111.12-1(c) - Prime movers.
(6) Subpart 111.105 of this part - Hazardous Locations.
(c) Cables that penetrate a watertight or fire boundary deck or bulkhead must -
(1) Be installed in accordance with 46 CFR 111.60-5 and meet the flammability-test requirements of either IEEE 1202 or Category A of IEC 60332-3-22 (both incorporated by reference; see 46 CFR 110.10-1); or
(2) Be specialty cable installed in accordance with § 111.60-2.